Detector de temperatura, adresabil, certificare, Panasonic
click pentru manualul de utilizare
The analogue heat detector 3308 measures the temperature through a thermistor. The temperature range is 0C to 100C in steps of 0.5C.
The address setting tool 3314 is used to set the detector's COM loop address. The detector has an Address label (Al) where the programmed address is to be written.
3314 is also used to set the detector mode.
NORMAL mode (analog): Detector 3308 + analog base 3312 used in the systems EBL128, EBL512 (SW version >2.x) and EBL512 G3. The detector works as a temperature sensor where the analog readings (0C to 100C) are converted to digital "sensor values" that are read and evaluated by the c.i.e. Algorithms for class A1, A2 S or B S (is set via Win128 / Win512 / WinG3).
2330 mode (conventional): Detector 3308 + analog base 3312 is used in the systems EBL512 / 1000 / 2000 as an equivalent to the 60C conventional fixed temperature heat detectors 6270 / 6275 + addressable base 2330, i.e. as a response grade 2 heat detector (static response temperature 57°C). NOTE! The analog base 3312 has no ext. line input, like the addressable base 2330 has.